Egress Marking Systems: Building Safety Regulations Guarantee Efficient Placement
The type of egress components used within your building greatly impacts the success of a defined evacuation plan. Placement determines the marking visibility to those occupying your building. Photoluminescent systems increase the reliability of an exit plan by providing visibility when backup systems fail. Its green glow remains present regardless of other environmental conditions. Having these products routinely installed in your building saves money, increases safety, and ensures guideline compliance. While purchasing them is the first step toward a more dependable evacuation, their placement is just as equally important. Egress marking systems are designed to provide full support of your defined evacuation plan. If they are not installed according to set guidelines, their effectiveness will be hindered, thus reducing the benefits of having them in place.
Self Luminous Safety Signs: Basic Recommendations Provided by the ICC
Self luminous safety signs may be purchased to notate exits, stairwells, fire equipment, individual floors, and obstacles within a building. Following the International Code Council (ICC) guidelines set for building and fire safety are one of the easiest ways to ensure every precaution is taken when applying luminous identifiers. Emergency exit symbols are required for every doorway leading to an exit. Additional signs may be used to show the corridor direction to the nearest egress location. Each item should be installed at a low level so it can be seen easily. Code requirements state that each sign cannot be more than eighteen inches from the floor. It should be horizontally centered on the door with the symbol having a height minimum of four inches. This placement ensures your occupants are provided visible assistance where smoke or other hindering factors are present.
Floor identification signs are necessary when occupants must exit multiple levels during an evacuation. These identifiers consist of stair, ramp, floor number, roof access, exit direction, and boundary locations for the beginning and endings of stairwells. They need to be placed approximately five feet from the landing area on each level. Signs must be at least eighteen by twelve inches with a minimum lettering size of one and a half inches. Level identifying numbers should be five inches in height in addition to all other lettering being one inch. Colors must contrast for increased visibility and a non-glare finish is recommended. Fire hoses, standpipes, extinguishers, rescue areas, and push to exit locations all have their own ICC placement guidelines. Photoluminescent markings can be applied to outline stairs or other dangerous areas. It is important to become familiar with these standards before installing your own self luminous safety signs.
The set guidelines have been created after extensive research of failed building evacuations and are designed to provide maximum visibility in critical situations. Following these suggestions will increase the chances of a safe evacuation for all residing in your building. Non-luminous alternatives do not offer the same reliability in thick smoke or no-light situations. Exit symbols also offer additional support in situations where electricity failures affect incandescent alternatives. ICC guidelines help you make an egress marking system highly effective. GloBrite supplies all the products you need to put a luminous system in place for enhanced building safety.